Question about Goodman GMS90703BXA Heater
My thermostat is set on 68, but the temperature rarely gets up to that and it blows out cold air all the time.
You may just have a dirty air filter or your furnace may be flashing an error code that could help you. Look for a small viewing port that looks into the cabinet of the furnace. Look for a blinking light. Count the blinks and then find the wiring diagram pasted to one of the panels. On the diagram it will have a diagnostic chart where you can look up the error code. Read on for some basic info that may help you.
On a call for heat, the 24 volt thermostat sends a signal to the control module. The control module will indicate a call for heat with a light on the control either blinking or remain solid depending upon model. The inducer (exhaust) blower will purge all gasses from the furnace and pressurize a pressure switch. Once the pressure switch tells the module to continue, the electronic ignition will energize and send 120 volts to the igniter. The igniter will glow and you will be able to see it if viewed thru the small inspection port. Once the igniter gets hot enough, it sends a signal to the module opening up the gas valve (24 volts). Either a pilot will come on or the burner tube will ignite then spread the flame to all burners. Lastly a safety sensor will be looking for a certain temperature within a few seconds and the furnace will continue to operate and the room air blower will turn on in a minute or two.
What could go wrong? The unit will not run if there is no signal from the thermostat (bad thermostat or broken wire), the control module does not sense a signal from the thermostat (bad control), the inducer does not energize (bad motor), the pressure switch does not close (blocked vent piping, bad switch, plugged condensate hose), the igniter does not energize (bad control, bad igniter), the gas valve does not open or there is no gas (bad gas valve, broken wire, no gas), the pilot does not light (dirty pilot), the burner does not light (bad burner, plugged orifice, not enough combustion air), the flame does not spread to each burner (bad flame spreader, dirty flame spreader, more bad burners), the flame safety sensor does not detect flame (dirty or bad flame spreader, bad flame sensor, broken wire, bad control), or the room air blower does not energize (bad fan motor, bad control).
Posted on Feb 09, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 12, 2015 | Honeywell Heat/Cool Thermostat
Oct 06, 2014 | Honeywell Heat/Cool Thermostat
Feb 04, 2011 | Goodman CLQ36AR49 Air Conditioner
Jan 08, 2011 | Honeywell Electronic Programmable...
Nov 07, 2009 | Ruud Central System Air Conditioner
Dec 18, 2008 | Honeywell Programmable Thermostat Heater
Nov 10, 2008 | Goodman PHKJ048-1 Air Conditioner
Jan 02, 2008 | GE Quiet-Aire Ductless Split System Air...
188 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: