Question about York Yankees Bedding MLB Comforter
Make sure the vent pipes that exhaust the fumes are not blocked in any way and also check the drain line to be sure it is not kinked from the vent motor to the trap. Take the hoses off the vent motor and the pressure switch and make sure all the hoses are clean and free from debris also check the trap on the drain hose and make sure it has water in it if it doesn't this will creat a negative pressure in the vent motor housing not allowing the vent pressure switch to make.
Posted on Feb 11, 2010
Hi, your description of whats happening is very helpful. We know your pressure switch is closing because without it the HSI wouldn't energize, so forget about the draft pressure switch. The problem is either the gas control valve or the control circuit board. To determine which, a volt meter is needed. After the HSI glows, you should have 24-27 volts ac going to your gas control valve. If you have the voltage but no gas, the valve is bad. If no voltage, the control board is defective. Best of luck.
Posted on Feb 11, 2010
Have you tried checking the flame sensor? The flame sensor senses heat from the HSI which then tells the controller to actuate the solenoid which controls the flow of gas. Try removing the flame sensor and cleaning with an emery cloth. Verify the electrical connections after reinstalling. If you still have problems I would say that the flame sensor is more than likely the culprit. Good luck!
I think it is the flame sensor because if your flame sensor worked and allowed the flow of gas to occur and you still didn't have ignition the furnace would go into lockout and require a power cycle at the breaker panel.
Posted on Feb 08, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 29, 2013 | Tools & Hardware - Others
Oct 08, 2012 | Heating & Cooling
Jul 02, 2011 | Heating & Cooling
Apr 12, 2011 | Heating & Cooling
Jan 11, 2011 | York Yankees Bedding MLB Comforter
Feb 20, 2010 | York Furnace Draft Inducer Blower Fasco #...
Feb 01, 2009 | York Yankees Bedding MLB Comforter
690 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: