Question about Heating & Cooling
I have an air handler (American Standard TWH030B14,0A,FA) mounted in the attic connected to a heat pump (Trane XE1000) mounted outside controlled by a thermostat (Trane Baystat 239) mounted in the family room. I want to upgrade the Trane Baystat thermostat controller to a digital controller. The controller has the following terminals with corresponding wire color in a counter-clockwise pattern:
X2 = Black
O = Orange
G = Green
Y = Yellow
T = Brown
R = Red
W = White
U = n/a
F = n/a
B = Blue
I want to use a Honeywell RTH7600D touch screen to replace the Trane Baystat 239. Can you advise the correct terminal placement from the Baystat to the Honeywell controller?
For Trane sytems, B is your "Common" wire. O is your reversing valve relay, G is your fan, Y is your compressor contactor, R is Hot, Brown will not be used on your electronic tstat. X2 is your backup electric heaters. Without knowing what terminals are on your new tstat, I cannot offer more information than this. The installation manual may indicate what each terminal is controlling. I strongly suggest to write down ALL of the terminals and colors from your old t-stat and be sure to turn off the power to your air handler. Put the fan switch on your tstat to ON before turning off the power. Make sure the fan is running. Then turn the power off to your Air Handler. If your fan stops running, you have turned the power off to your tstat and are ready to start replacing it with your new tstat. I hope you find this helpful. Good Luck!!!
Posted on Feb 07, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
May 08, 2017 | Honeywell Heating & Cooling
Feb 28, 2015 | American Standard Heating & Cooling
Mar 26, 2017 | Heating & Cooling
May 23, 2010 | Honeywell Focus 6300B 5-2 Days...
Oct 16, 2009 | Heating & Cooling
Jul 11, 2009 | Honeywell Programmable Thermostat Heater
May 30, 2009 | Heating & Cooling
May 11, 2008 | Heating & Cooling
Sep 28, 2007 | Heating & Cooling
1,786 people viewed this question
Usually answered in minutes!