Question about Goodman PHKJ048-1 Air Conditioner
What are the testing procedures for the elements etc.
Basically, set unit to call for the heat strips to be energized. There should be a control that sends power to the heat strips. Usually a contactor or relay. Verify that power passes thru this device to the heat strips. Make sure that the correct voltage is being delivered to the heat strips. If correct voltage is present at the terminals of the heat strip, check the amps. If no amps, heat strip is probably broken. Don't forget that some of these units have sequencers that "Stage" the energizing of the strips. And all of them should have some safety device such as a fuse or thermal overload or some other device that stops voltage should there be a malfunction.
Hope this helps.
Posted on Feb 06, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 21, 2014 | Goodman Heating & Cooling
Nov 29, 2013 | Goodman Manufacturing Goodman GPH1530M41...
Nov 11, 2013 | Goodman Manufacturing Goodman...
Jul 21, 2011 | Goodman Heating & Cooling
Feb 02, 2011 | Goodman Heating & Cooling
Mar 14, 2009 | Goodman CLQ36AR49 Air Conditioner
Dec 31, 2008 | Ovens
Feb 07, 2007 | Goodman PHKJ060-1 Air Conditioner
Jan 24, 2007 | Goodman GMS90703BXA Heater
Dec 11, 2011 | Goodman PHKJ048-1 Air Conditioner
345 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: