Question about Honeywell Programmable Thermostat Heater
If flames go on and then go right out it is usually a flame sensor problem. These are usually found on newer furnaces with electronic ignition systems. It will be located in the flames of the burner farthest away from the ignitor. If you see an orange glow before the flames light then thats it! If ignitor is on the right side then flame sensor is at the opposite end. It is a round steel probe with a white ceramic top and a wire running to it that sits in the flame and is a little bigger round than a coat hanger. Shut off power, wait to make sure it is cool to the touch, using a piece of steel wool( or sandpaper if none available) give it several good strokes to clean it. You may have to remove it from the top by removing the screw and pulling it out. I usually can clean them without removing them but I have small hands! Turn power back on and it WILL run if that was the problem!!!!!!
Posted on Feb 04, 2010
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Nov 16, 2014 | Heating & Cooling
Jan 09, 2014 | Amana Heating & Cooling
Oct 12, 2013 | Heating & Cooling
Jun 08, 2017 | Heating & Cooling
Feb 10, 2011 | Coleman Heating & Cooling
Jan 02, 2011 | Heating & Cooling
Oct 24, 2010 | Dayton Gas Furnace Heater
Jan 11, 2010 | Heating & Cooling
Jan 16, 2009 | Hunter Fan Company 5/1/1 Programmable...
Jun 29, 2016 | Honeywell Programmable Thermostat Heater
844 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: