Question about Heating & Cooling
Remove red and white wire from t-stat and connect if it starts then it is t-stat.
if not jump out at furnace where wires connect to it.
could be an inducer motor problem?
Posted on Feb 04, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 19, 2016 | Heating & Cooling
Nov 01, 2015 | Heating & Cooling
Jan 21, 2015 | Heating & Cooling
Jun 16, 2014 | GE Zoneline Deluxe Series Cooling &...
May 14, 2014 | Comfortmaker C4A348GKD 4 Ton 14 SEER AC
Jan 12, 2011 | Ruud UAPA024 Air Conditioner
Sep 23, 2010 | Ruud Heating & Cooling
Dec 06, 2009 | Ruud UAMB042 Air Conditioner
Oct 24, 2008 | Ruud UBHC Air Conditioner
123 people viewed this question
Usually answered in minutes!