Question about Carrier XHB123D X/Y Series Heat/Cool Air Conditioner
Blower comes on, pilot lights, burners ignite, big blower comes on but the burners and pilot go out then the blower goes off before the house gets warm,
thermostat is set for 74 goes off at 64 will not come on again until i turn the thermostat off then back on but keeps going off before it reaches the correct temp
The flame detector rod is dirty? try cleaning with sand paper and scraping also. there should be a small amp. reading threw wire coming from flame detector rod. in milli amp range. increases when running. some times i use a jumper to hold gas valve on once started to allow time to test amps.
Posted on Feb 21, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 29, 2013 | Carrier XHB123D X/Y Series Heat/Cool Air...
Mar 29, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Mar 13, 2010 | Carrier Heating & Cooling
Jan 10, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Jan 01, 2010 | Carrier XHB123D X/Y Series Heat/Cool Air...
Dec 24, 2009 | Carrier Heating & Cooling
Nov 28, 2009 | Carrier 38CKC042 Air Conditioner
Nov 16, 2009 | Carrier XHB123D X/Y Series Heat/Cool Air...
Nov 06, 2009 | Heating & Cooling
Oct 22, 2008 | Carrier XHB123D X/Y Series Heat/Cool Air...
807 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: