Question about Kidde 1275 Hardwire Smoke Alarm with Hush Feature and Battery Backup, Contr
Replaced 9 v batteries, unit's green light is on, but units continue to chirp to each other. Hard wired, installed in new construction early 2004
This is the troubleshooting information from the kddie site. The problem is usually related to an older battery or improperly installed battery. You might also have to do a reset as described below. If battery and cleaning don't work, it might be time for a replacement - short money to keep you and your home safe.
Verify that a battery of the recommended type is securely installed. Make sure to use a battery with a use-by date no later than four to five years in the future. Check that the battery is snapped in completely so it cannot be shaken loose. It’s possible that battery connections may not be making good contact with the battery. Disconnecting and re-connecting the battery once or twice will likely fix this condition. On units with a front-load battery, be sure that the battery compartment door is closed completely as well. Loose white neutral wire can cause an echoing chirp. (From one unit to the next)
Dust and insects can collect in the sensing chamber of the alarm. An accumulation of dust in the sensing chamber can cause the unit to chirp. It is good practice to clean the smoke alarm when you change the battery. Static electricity from the ac quick connector attracts dust and can cause false alarms.
Cleaning smoke alarms:
To clean your alarm, remove it from the mounting bracket as outlined here. You can clean the interior of your alarm (sensing chamber) by using compressed air or a vacuum cleaner hose and blowing or vacuuming through the openings around the perimeter of the alarm. The outside of the alarm can be wiped with a damp cloth. After cleaning, reinstall your alarm, verify the green LED is on and test your alarm by using the Test Button. If cleaning does not restore the alarm to normal operation, the alarm should be replaced.
Some current model smoke alarms have a processor that retains certain error conditions, such as a weak battery. The error condition should reset when the battery is replaced but sometimes it does not and must be manually reset to clear the error.
To reset an AC unit with a battery backup:
Turn off the power to the smoke alarm at the circuit breaker.Remove the smoke alarm from the mounting bracket and disconnect the power. Remove the battery. Press and hold the test button for at least 15 seconds. The unit may chirp or alarm for a few seconds before going silent.Reconnect the power and reinstall the battery. The unit will chirp once when the power is restored and should not chirp afterwards.
To reset a DC only unit:
Remove the battery. Press and hold the test button for at least 15 seconds. The unit may chirp or alarm for a few seconds before going silent.Reinstall the battery. The unit will chirp when the battery is first connected but should not chirp afterwards.
If the AC power to the unit is interrupted, the unit will chirp when the power is restored. This could be caused by power surges. If the chirping seems to occur at about the same time in the evening or morning, it could be due to a surge created when the power company switches electrical grids to meet demand. Check to see if the chirp (or chirping) occurs when something else in the house is turned on such as an exhaust or attic fan, a heater, etc. If the smoke alarm is connected to a circuit with such a device, the alarm may chirp when the other device is switched on. If this is the case and the device is plugged into a wall outlet, move it to another outlet on a different circuit. If it is a hardwired device, have an electrician investigate it. These conditions can be minimized by installing your alarms on a dedicated circuit in compliance with NFPA requirements.
If none of these conditions exist and the suggestions don't alleviate the symptom, the alarm should be replaced. Age may be a factor. Smoke and heat alarms should be replaced every 10 years, and carbon monoxide and combination alarms should be replaced every 7 years. Most of our alarms have a 5 year warranty from date of purchase (check your user manual for details). A date code is stamped on the label attached to the back of the unit.
Posted on Mar 23, 2010
Which ever unit set the system off is the one you reset,should stop the chirpping.
Posted on Feb 13, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
New users get to try the service completely Free afterwhich it costs $6 per call and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 27, 2016 | Cars & Trucks
May 15, 2016 | First Alert SA302 Dual System Smoke...
Oct 16, 2015 | Home
Apr 29, 2014 | APC BE500U ES 500 USB BACK-UPS 500VA/300W...
Jan 06, 2013 | Kidde Firex I4618 Smoke Alarm W/battery...
Sep 07, 2011 | Kidde 21007581 120v Firex 4618 Pro Basic...
Nov 15, 2010 | Kidde 4618 Firex Hardwire Ionization Smoke...
Nov 20, 2009 | Home Security
Jan 13, 2008 | UN 3000SW Radar Detector
May 22, 2014 | Kidde 1275 Hardwire Smoke Alarm with Hush...
2,655 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: