Question about Saniflo 013/003/005 Sanibest Toilet with Grinder Series Pump in White Round
The Sanibest has a pressure sensitive switch that activates when the water pressure inside the unit gets to a particular level. It is basically a microswitch sealed in a watertight container.
If the Sanibest has got gunked up inside it is possible that the unit is not kicking in soon enough and the water is backing up into your shower.
Another possible issue is that something has got into the Sanibest that should not be there that is impeding the flow out of the unit.
For both cases I would suggest that you empty the cistern and WC bowl after running clean water through th unit for a few miunutes (makes the job a bit less horrible!).
You could also try and use SaniFlo cleaning product and hope that it clears the potential blockage http://www.sanifloproducts.co.uk/products/Saniflo-Products-Saniflo-Descaler.html
** ENSURE THAT THE VERY FIRST THING YOU DO IS TURN OFF POWER TO UNIT **
1. Turn off the electricity to the unit (should be on a fused spur)
2. Disconnect the pipes (inlet and discharge) - you may get a bit of surplus water coming out so have some sponges and a bucket ready.
3. Disconnect the wiring and take the unit out
4. I clean my Saniflo's outside with warm bleach water ..
- Wear rubber gloves to keep germs out of any cuts you may have / get on your hands
- Put the elextrical cable in a taped up plastic food bag or similar to keep dry
- undo the 'star screws'
- Flip up the plastic retaining tabs with a flat blade screwdriver and gently ease the lid up.
- I put bleach and warm water in, leave it for a while (30 mins) and then swish it around and empty out into an outside drain etc
- If you want to use an old toothbrush to get into the areas by the float switch and under the motor it does help. I also used a hosepipe in the past which did the trick.
- Also pay attention to the inlet port and the actual pipes under your sink for gunk
put it back together, aligning the seal and plastic clips should just pop on (may need a firm push). Do up star screws and you are ready to reconnect the pipes and electrics.
I use some tissue paper to check for any leaks around the pipes just to be sure!
Another point to note is that you can insert a simple non-return valve into the pipe near the shower to stop the water coming back up; however this is not addressing the root cause.
Hope this helps - if so, please leave feedback. If not let me know and I'll try and help some more!
Posted on Feb 02, 2010
a 6ya Repairman can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repair professionals here in the US.
click here to Talk to a Repairman (only for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 05, 2017 | Home
Nov 13, 2016 | Plumbing
Mar 13, 2015 | Home
Jun 17, 2013 | Home
Mar 22, 2013 | Saniflo & Saniplus& Macerator Pump
Aug 06, 2010 | Home
May 12, 2010 | Grohe Integrated 1/2'' Shower Thermostatic...
Feb 05, 2010 | Saniflo Sanibest Grinder Pump Only 013
Dec 28, 2008 | Home
Sep 06, 2008 | Home
394 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: