Question about Heating & Cooling
I have a Whirlpool furnace model #nuge080kg01. The furnace is running, but the blower is never kicking in. I called my personal expert (my dad) and he says there should be a blower motor reset switch. I'm not finding it...any thoughts? I can see the fan itself and I can grab the stick sticking out the back of the fan and turn the blades...he says it might be in a hole but I don't see anything at all.
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
first off buy yourself a honeywell stat, in my personal opinion lux stats are garbage, I have run into so many that are bad stats !!! but as far as your fan not shuting down, sounds to me like your fan center on your circuit board is bad and will not shut down the fan when needed, you will have to replace the circuit board, as the fan center is a part of the whole of the circuit board, hope that helps
Posted on Jan 20, 2009
I wouldnt have said it was the thermo-sensor thingie.
When you are switching the breaker on and off you are reseting the furnace and it will start the heating cycle again. It sounds like your blower motor is not working so the furnace heats up but because the fan never kicks in the furnace is overheating and shutting off. sit by your furnace while it is on and see if you can hear the motor? if you cant hear the motor but the burners are on then you most likely need a new motor. please note that it is normal when the burners first kick in there will run for a couple of mins before turning the fan on. If the furnace is belt driven then you might need new bearing or belt. give me the name and year of the furnace and i should be able to help more.
Posted on Feb 12, 2009
could be a relay possible fan motor try put the fan to on on the thermostat if no fan one of the two relay or fan motor. you'll need a volt meter and know how to use it to solve problem It would be safer to call a contractor. Tom
Posted on Jun 18, 2009
Yes. If the high limit is tripped, the furnace will bring on the fan continuously until the limit resets. Often, they will not reset if tripped repeatedly. If the furnace is too large for your application, you probably are not able to move enough air to keep the heat exchanger cool enough.
Posted on Oct 03, 2009
Tips for a great answer:
Feb 26, 2014 | Emerson Lennox Ducane Armstrong Furnace...
Mar 16, 2013 | Heating & Cooling
Nov 21, 2011 | Coleman Mach III Air Conditioner
Apr 12, 2017 | Heating & Cooling
Dec 29, 2009 | Heating & Cooling
Nov 28, 2009 | Tools & Hardware - Others
Oct 04, 2009 | Heating & Cooling
Feb 19, 2009 | Aprilaire 550 Humidifier
Nov 10, 2008 | Goodman GMS90703BXA Heater
176 people viewed this question
Usually answered in minutes!