Question about Omega Trane Furnace Draft Inducer Blower 115 Volt Variable Speed Fasco # A190
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
THIS IS A COMMON PROBLEM WITH THE DOOR SWITCHES, MY FIRST ANSWER WOULD BE REPLACE THE SWITCH SECOND WOULD BE OPEN THE DOOR AND PUSH THE BUTTON IN AND SEE IF THE FURNACE WILL WORK. THIS SWITCH IS JUST A DOOR SAFTEY IF THIS WORKS. I HAVE TAPED A PIECE ON THE INSIDE OF THE DOOR WHERE THE SWITCH WILL HIT THE DOOR ABOUT A 1/4 INCH THICK AND SEE IF THIS WILL GET YOU RUNNING UNTILL YOU CAN GET A SWITCH
Posted on Oct 12, 2009
need help with gas furnace put in new presure switch and it worked for a while now i have to blow into it to get it to turn on ignitor .
Posted on Dec 10, 2009
When a furnace is replaced with a newer style unit like yours with an inducer motor, they sometimes use the old vent pipe. These old style vent pipes are transite (light weight cement), the moisture created from your furnace exhaust is caught on the cool transite surface and runs back down into the blower blades or wheel bringing a white mineral deposit with it which causes your problem. The vent should nave been replaced with the heater using a metal vent material. You will need to replace your inducer motor assembly and vent pipe to prevent a recurrence.
Posted on Dec 30, 2009
Tips for a great answer:
Nov 27, 2016 | Heating & Cooling
Feb 19, 2016 | Carrier Heating & Cooling
Jan 08, 2015 | Emerson Lennox Ducane Armstrong Furnace...
Dec 04, 2013 | Cars & Trucks
Feb 17, 2013 | Tools & Hardware - Others
Mar 02, 2011 | Heating & Cooling
Dec 04, 2010 | York Furnace Draft Inducer Blower Fasco #...
Jan 20, 2010 | Fasco GSW Hot Water Heater Exhaust Draft...
Oct 25, 2008 | Heating & Cooling
420 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: