Question about APC Smart-UPS 1000VA UPS System
UPS's by and large are maintenance free beasts meaning there's not a whole lot you can do to fix them. In my experience if one fails it's usually the battery. If it's not the battery then the whole unit is replaced. As you unit is new I'd recommend simply taking it back for a new one, or getting hold of a new battery to try. You test the battery theory if you have another of the exact same model and borrowing the battery.
Hope this helps,
Posted on Feb 01, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 15, 2012 | Tripp Lite Tripplite Omniplus 1000 LCD UPS...
Oct 18, 2011 | APC Smart-UPS 1000XLI (SUA1000XLI) UPS...
Sep 25, 2011 | APC Smart-UPS 1000VA UPS System
Sep 20, 2011 | APC Smart-UPS 1000VA UPS System
Automatic: The UPS performs a self-test automatically when turned on, and every
two weeks thereafter (by default). During the self-test, the UPS briefly operates the
connected equipment on battery.
Manual: Press and hold the button for a few seconds to initiate the self-test
REPLACE BATTERY LED ILLUMINATES
Replace Battery LED flashes and
short beep is emitted every two
seconds to indicate the battery is
Check that the battery connectors are fully engaged.
Weak battery. Allow the battery to recharge for 24 hours. Then, perform a self-test. If the
problem persists after recharging, replace the battery.
Failure of a battery self-test. The UPS emits short beeps for one minute and the Replace Battery LED
illuminates. The UPS repeats the alarm every five hours. Perform the self-test
procedure after the battery has charged for 24 hours to confirm the Replace
Battery condition. The alarm stops and the LED clears if the battery passes the
Sep 09, 2011 | APC Smart-UPS RT 5000VA (SURTD5000XLI) UPS...
Aug 14, 2011 | APC Smart-UPS RT 10000VA - UPS ( external...
Jul 01, 2010 | Tripp Lite (OMNIVSINT1000) UPS System
Apr 08, 2010 | APC Smart-UPS 1000VA UPS System
Feb 19, 2010 | Tripp Lite OMNIVS1000 UPS System
Apr 01, 2009 | APC Smart-UPS 1000VA UPS System
Jun 26, 2017 | APC Smart-UPS 1000VA UPS System
179 people viewed this question
Usually answered in minutes!