Question about Williams Heating & Cooling
Take the red and white wires going to your thermostat and jump them together. If the unit starts, you have a bad thermostat. If not, at the furnace, jump out the terminals where the thermostat wires are connected to. If the unit starts, you have a bad thermostat wire or connection. If not, you will need to check for 24 volts at the gas valve while the thermostat is calling for heat. If yes, bad gas valve. If no, bad transformer.
Posted on Jan 31, 2010
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 14, 2015 | Heating & Cooling
May 23, 2014 | Jandy Lite 2 Natural Gas Pilot Light...
Feb 19, 2018 | Desa International Heating & Cooling
Sep 30, 2011 | Heating & Cooling
Apr 19, 2010 | Vanguard International Blue Flame - Large...
Oct 20, 2009 | Heating & Cooling
Sep 27, 2009 | Pentair Minimax Ch 400,000 Btu Propane...
May 02, 2009 | Pentair Minimax CH Heater
Dec 18, 2008 | Endless Summer gwt501a Open Flame Patio...
486 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: