Question about Goodman Heating & Cooling
Bad gas valve, no gas getting to gas valve, restriction in air intake, bad electrical connection from board to gas valve, or a bad board. Make sure you have gas at other gas appliances. Weather changes could cause a regulator to stick closed (your gas company is responsible for that). You can always tap lightly on the gas valve in the furnace to dislodge any debris holding the valve closed. Make sure the switch position on the gas valve is on. Remove and reinstall the wires to the gas valve to make sure they have a good connection. Remove the air intake pipe (not the exhaust) or open up any access to the burner to allow a good air supply to the burner. Lastly, follow the wiring from the gas valve to the board. Remove the plug from the board and inspect for any corrosion.
Posted on Jan 31, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Apr 17, 2015 | Heating & Cooling
Feb 11, 2013 | Heating & Cooling
Nov 19, 2012 | Goodman Heating & Cooling
Jul 15, 2011 | Kitchen Ranges
Mar 01, 2011 | Heating & Cooling
Jan 27, 2011 | Goodman Heating & Cooling
Dec 11, 2009 | Coleman Heating & Cooling
Oct 20, 2009 | Ruud UBHC Air Conditioner
Jan 18, 2009 | Coleman Propane Forced Air Heater...
139 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: