Question about Honeywell HE365 Humidifier
I get no water through the selinod. I replaced it and still no water. I get no voltage at the connector of the selinod. What is next.
First check to see if you have power at the transformer, that controls the humidifier. If you have 24v there, check to make sure you have 24v going into the humidistat, and 24v leaving the humidstat. If all this is correct, and the solenoid is not getting power, you may have an isolation relay wired into the blower motor (only in some applications) that has gone bad. Check the blower cabinet for this relay. Hope this helps
Posted on Jan 30, 2010
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 22, 2013 | Humidifiers
Jan 05, 2013 | Honeywell HE220A1019 Whole House...
Aug 18, 2012 | Aprilaire 550 Humidifier
Jun 24, 2011 | Crane Adorable Humidifiers 1-Gallon...
Mar 04, 2011 | Aprilaire 700 Humidifier
Jan 17, 2011 | Aprilaire 400 Humidifier
Mar 14, 2010 | Humidifiers
Dec 03, 2009 | Aprilaire 600 Humidifier
Apr 09, 2009 | Aprilaire 700 Humidifier
Mar 14, 2009 | Kenmore Humidifiers
Jan 09, 2011 | Honeywell HE365 Humidifier
395 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: