Question about Dayton (4LX41) Heater
UNIT WILL NOT STAY RUNNING UNLESS PRESSURE SWITCH IS JUMPED, AFTER IT IS JUMPED THE UNIT WILL RUN FOR 10-15 MIN. THEN IT WILL LOCK OUT ON HIGH LIMIT, FAN IS STILL RUNNING.
Exhaust is restricted or crack in heat exchanger. Get someone to look at it!
Posted on Feb 14, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 28, 2014 | Dayton Heating & Cooling
Nov 24, 2012 | Dayton Gas Furnace Heater
Oct 20, 2011 | Dayton Gas Furnace Heater
Nov 20, 2010 | Heating & Cooling
Feb 09, 2010 | Dayton (3E379) Heater
Feb 06, 2010 | Dayton Gas Furnace Heater
Dec 12, 2009 | Dayton Heating & Cooling
Dec 04, 2009 | Dayton Heating & Cooling
Nov 17, 2008 | Dayton G73 Utility Heater
Feb 19, 2008 | Dayton E52 Utility Heater
216 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: