Question about Aprilaire 600 Humidifier
When I put it into test mode recently i thought I heard something snap. Ever since that snap I cannot get the solenoid to click and there seems to be no water supply at all. Any suggestions? I thought maybe I needed to take the cover off the humidstat and see if something needed to be reconnected. Not sure though.
Your solenoid may have seized. The best way to check is remove the cover off the humidifier pad housing, remove the rubber tube of the distribution tray and see if water comes out while in the test mode. If you have a volt meter you can test to see if you have 24volts at the two wires connected to the solenoid. If you have 24volts there but no water ,the solenoid is bad if not you may have a bad humidistat or humidifier transformer depending on how it is wired.
Posted on Mar 04, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 13, 2011 | Aprilaire Humidifiers
Jan 15, 2011 | Aprilaire 600 Humidifier
Dec 21, 2010 | Aprilaire 600 Humidifier
Jan 06, 2010 | Aprilaire 600 Humidifier
Dec 07, 2009 | Aprilaire Humidifiers
Nov 27, 2009 | Aprilaire 600 Humidifier
Oct 12, 2009 | Aprilaire 700 Humidifier
Feb 22, 2009 | Aprilaire 600 Humidifier
Jan 16, 2009 | Aprilaire 700 Humidifier
Jan 14, 2009 | Aprilaire 600 Humidifier
May 22, 2017 | Aprilaire 600 Humidifier
1,371 people viewed this question
Usually answered in minutes!