Question about Heating & Cooling
THERE IS A TUBE OR CHANEL FROM THE FRONT EVAPORATOR DRAIN PAN THAT RUNS TO THE BACK OF THE UNIT INTO THE CONDENSER PAN. IT IS ALWAYS ADVISABLE TO THOUROUGH LY CLEAN ALL COILS, AND DRAIN PANS AND DRAIN LINES ANUALLY. IF THAT TUBE OR CHANEL WAY GETS PLUGGED IT WILL CONSTANTLY DRIP IN THE COOL MODE.,
IF YOUR A/C IS 110V MOST ALL ARE ABOUT 5,000 - 7,000 BTU''S ALL SHOULD RUN ON A SEPERATE CIRCUIT OR NOT HAVE ANYTHING ELES PLUGED IN ON THAT CIRCUIT.
MOST ALL WINDOW UNITS HAVE THE BTU'S RATING ON THE TAG INSIDE THE UNIT. THESE SMALL UNITS REQUIRE COMPLETE REMOVAL FROM THE WINDOW OR WALL FOR CLEANING. ONLY LARGER UNITS 10,000 AND ABOVE SLIDE OUT OF THE CABINENT FROM THE FRONT.
90% OF A/C I HAVE REPAIRED IN 40+ YEARS WERE DUE TO PLUGGED DRAIN LINES A DIRTY COILS. THEY MUST BE ALL CLEAN BEFORE I COULD START TO DIAGNOSE ANY PROBLEM BECAUSE THE PRESSURES VARY IF THE COILS ARE RESTRICTED WITH DIRT, ETC.
Posted on Feb 08, 2008
Ther is no drtain in the back !!! The water that drains to the back drains into a pan below the condenser coil wher the "Slinger-Ring" around the rear fan blade picks up the water and sprays it on the hot coil outside to help cool-it down.
Posted on Feb 09, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 21, 2014 | Carrier Heating & Cooling
Jun 15, 2011 | Sanyo Heating & Cooling
Feb 03, 2011 | Heating & Cooling
Jul 13, 2010 | Carrier BCA101R Air Conditioner
Dec 06, 2009 | DeLonghi Heating & Cooling
Nov 26, 2009 | Samsung Heating & Cooling
Aug 02, 2009 | Heating & Cooling
Jun 08, 2009 | Panasonic Room Air Conditioner CWXC104HU
May 23, 2009 | LG Heating & Cooling
985 people viewed this question
Usually answered in minutes!