Question about Freezers
Why would you want to mount a potential relay in the direction specified on the relay? example if it says "this side down" what would it hurt to turn the down side up? the relay is being used in hvac
These relays are calibrated in a specific direction to open the contacts. When you hang it upside down or sideways you are changing the calibration. This may not allow the relay to function as required and keep the start capacitor and start winding in the motor engaged longer than necessary. Long term this could cause no starts and failed relays and start capacitors and in the worse case a failed motor.
Posted on Feb 25, 2008
Possibly to avoid the possibility of water pooling on top of it and thus allowing the water to seep inside of the relay and kill it.
Posted on Feb 12, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 06, 2015 | Maytag 20 cu. ft. Upright Freezer MQU2056B
May 14, 2014 | Scotsman Freezers
Apr 04, 2012 | True 72 cu. ft. / 2039 liter Commercial...
Jan 04, 2012 | True Freezers
Mar 31, 2011 | Master Bilt Commercial Freezer 860610
Jul 09, 2010 | Maytag Freezers
Aug 10, 2009 | Frigidaire Freezers
Feb 22, 2009 | True 72 cu. ft. / 2039 liter Commercial...
Nov 19, 2008 | Frigidaire 20.6 cu. ft. / 583 liter...
Apr 19, 2017 | Samsung RS261MD 26 cu. ft. Side by Side...
421 people viewed this question
Usually answered in minutes!