Question about Heating & Cooling
So It turns on for a few seconds and then turns off again. While its on, it blows warm air just fine and all that its just that it only stays on for 5 seconds at the most.
I am a furnace technician and to solve the problem.You will find on the opposite side of the ignitor their is a flame rod with a wire connected to it.Remove it and clean it with sandpaper and re install it and it should fix the problem.If this is dirty it won't sense ignition and the board thinks that is it introducing raw gas into furnace and it isn't igniting and shuts off as a safety precaution.If you see a blueish tinge on the flame rod you should probably replace it.
Posted on Aug 19, 2008
Check the flu. It has an outer pipe for fresh intake air and an inner pipe that allows the cumbusted air vent out. If the inner pipe is rusted through it sucks the combusted gas back into the fresh air side and flame dies off due to the lack of oxygen and shuts off the gas valve.
Posted on Jan 01, 2009
Gas direct vent units such as these (not sure what model you have) typically have a thermocouple, or if the thermostat is mounted away from the unit, a thermopile. Either of these could be defective or in some cases, the valve is bad. Make sure there is no obstruction at the vent outside as well, as this will cause the unit to shut off due to lack of combustion air.
Posted on Feb 04, 2008
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 28, 2016 | Coleman Heating & Cooling
Oct 08, 2014 | Coleman Home Electric Furnace Eb15b/Eb15d
Jan 29, 2014 | Goodman GMS90703BXA Heater
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Jan 28, 2011 | Coleman Heating & Cooling
Nov 24, 2010 | Coleman Propane Forced Air Heater...
Oct 25, 2009 | Heating & Cooling
Oct 07, 2009 | Carrier Heating & Cooling
Mar 30, 2009 | Coleman Heating & Cooling
Jan 21, 2009 | Coleman Propane Forced Air Heater...
2,559 people viewed this question
Usually answered in minutes!