Question about Heating & Cooling
Why would my air condtioner be leaking from the wall unit?
There normally two types of leakages from the wall unit.
1.The warm air in the room when comes in contact with the cooling coil of heat exchanger (consisting of fine fins where compressed refrigerant evaporates) looses its heat & cannot retain the same moisture content at lower temperature at the point of contact with evaporator. There is a provision of a drain pipe to carry this condensed water to outside water drain. So if the drain pipe is choked or the coupling joint of the drain pipe at the bottom of cooling coil is not proper, there will be water leakage, This can be easily attended by physically looking at the fittings.
2.The second problem can be the leakage of the refrigerant. If there is second type of problem, then there will be very little or no cooling irrespective of continuous running of air conditioner. This can be easily checked by feeling the temperature of outlet air from the air conditioner.
Conclusion-As you have written that there is leakage from the air conditioner, but you have not written whether it is visible or invisible. If the leakage is visible, it is problem number 1 & if it is invisible, it is problem number 2.
If you are not satisfied you are free to ask for more explanations.
Posted on Jan 29, 2008
If it is water leaking check the indoor drain pan if overflow with water.If the pan is overflow with water then you need to clean your drain pan and drain pipe. While the unit is operating check the drain pipe if water drip, if no water coming out from drain pipe you need to flush it with water to flush out the restriction.
Try also to check if no icing build in the evaporator fins. If icing is present then you need to clean your indoor evaporator pins and air filter. But if it is clean and still icing is present then your unit is out of gas.
Posted on Jan 29, 2008
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 10, 2010 | Sanyo Split System Air Conditioner
May 28, 2010 | LG Art Cool LA121CNP wall/window Air...
Jan 16, 2010 | GE Quiet-Aire Ductless Split System Air...
Jan 09, 2010 | Mitsubishi MS-A09WA Split System Air...
Nov 30, 2009 | Heating & Cooling
Nov 10, 2009 | LG Art Cool LA091HNP Split System Air...
Aug 03, 2009 | GE Quiet-Aire Ductless Split System Air...
Mar 16, 2009 | 1999 Daewoo Nubira
Feb 15, 2009 | Mitsubishi MS-A09WA Split System Air...
1,471 people viewed this question
Usually answered in minutes!