Question about Aprilaire 550 Humidifier
Did you just install this unit, or has it been working for a while and just stopped?
1. If you just installed it, the solenoid wires (yellow) must be hooked up to switch in when you have a call for heat.
a) use a current sense relay OR
b) connect 120V & neutral to "HUM" terminal and neutral on heater control board.
2. If it has worked before, maybe the saddle valve is plugged. Turn the "T" handle all the way clockwise, then all the way out CCW. You can hear the water start flowing. Loosen compression fitting at solenoid valve to make sure water is getting there.
3) Also, you must supply 24V to the circuit to open the solenoid valve. Check your wiring. It depends on the model what way to wire it and I cannot go into that here.
4) Testing: Turn off humidistat control. Turn on heat, wait for blower to come on. Turn humidistat control to test posn. Solenoid valve should click. This will put water into top of Aprilaire tray, after few minutes it will dribble out bottom clear vynl tube to the
Posted on Jan 29, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 30, 2013 | Aprilaire 700 Humidifier
Feb 18, 2011 | Aprilaire 550 Humidifier
Jan 17, 2011 | Aprilaire 400 Humidifier
Jan 10, 2011 | Aprilaire 700 Humidifier
Feb 27, 2010 | Aprilaire 600 Humidifier
Feb 19, 2009 | Aprilaire 550 Humidifier
Jan 25, 2009 | Humidifiers
Jan 24, 2009 | General Filters 1042-LH Humidifier
Dec 20, 2008 | General Filters 1042-LH Humidifier
169 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: