Question about Heating & Cooling
Could be the thermostat or the low voltage line to the outside. Usually a dog chews through it or the weedeater hits it and breaks connection. Turn on cool, go outside and see if it gets 24 volts to the two wires going to contactor (have to take off cover to get to it) DO NOT TOUCH THE CONTACTOR IT HAS 240 V AT ALL TIMES, unless disconnect is thrown, so turn it off. If you aren't getting anything, then it's either the low voltage wire broken somewhere or the thermostat malfunctioning. Make sure you turn off the inside unit before messing with thermostat or you will pop the transformer. If it pulls the contactor in, and you still aren't getting anything, then check for voltage on the load side of contactor (opposite from the inlet or lead side). If you are and you hear a hum from the compressor and the condensing fan motor is running, then it's your compressor. You'll have to remove the top cover to do the next step. Check to see if it when to ground by using a meter set on resistance and with the connector to the compressor removed, put one lead on one of the copper pipes going up to it and touch the other lead against any or all of the pinouts on the compressor. If you get a reading, it went to ground and you will need a new compressor or whole new condensing unit, depending on the age of the one you have now.
Posted on Jan 27, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 24, 2011 | Heating & Cooling
Feb 24, 2011 | Pace 18HPEWHEC Split System Air...
Feb 02, 2011 | Heating & Cooling
Dec 11, 2010 | Fujitsu Heating & Cooling
Oct 06, 2010 | DeLonghi Heating & Cooling
Oct 30, 2009 | 1997 Jeep Grand Cherokee
Feb 02, 2009 | Heating & Cooling
139 people viewed this question
Usually answered in minutes!