Question about Goodman GMS90703BXA Heater
On - OK
1 Blink - Ignition failure. Check Gas flow, gas pressure, gas valve, flame sensor.
2 Blinks - Closed pressure switch. Check pressure switch (stuck in closed position).
3 Blinks - Pressure switch - failre to close. Check venter, pressure switch, vent blockage.
4 Blinks - Open limit switch. Main limit or aux limit are open. (My comment - Means overheating in chamber. Often result of blocked intake air. Bad filter. In my case, plastic wrap had been sucked into the intake. )
6 Blinks - False flame sensed. Check sticking gas valve.
Rapid continuous blinking - Incorrect twinning, incorrect primary polarity. Reverse transformer secondary leads, reverse primary wires.
Closed pressure switch can be from dirty combustion vents, bad chamber pressure - like missing screws, maladjusted gas pressure, failing pressure switch, loose hoses, moisture in the hoses or fan blades The switch need to be closed to ge the unit to work
Posted on Jan 23, 2008
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Oct 24, 2015 | Heating & Cooling
Jan 21, 2015 | Frigidaire PTAC Electric Heat 9000 BTUs...
Jan 19, 2015 | Armstrong Lennox Ducane Armstrong Gas...
Oct 28, 2011 | Goodman Heating & Cooling
Oct 12, 2011 | Goodman GMS90703BXA Heater
May 15, 2011 | Heating & Cooling
Jun 17, 2010 | Heating & Cooling
Mar 12, 2010 | Heating & Cooling
Dec 01, 2008 | Heating & Cooling
May 14, 2008 | Heating & Cooling
1,454 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: