Question about Goodman GMS90703BXA Heater
On - OK
1 Blink - Ignition failure. Check Gas flow, gas pressure, gas valve, flame sensor.
2 Blinks - Closed pressure switch. Check pressure switch (stuck in closed position).
3 Blinks - Pressure switch - failre to close. Check venter, pressure switch, vent blockage.
4 Blinks - Open limit switch. Main limit or aux limit are open. (My comment - Means overheating in chamber. Often result of blocked intake air. Bad filter. In my case, plastic wrap had been sucked into the intake. )
6 Blinks - False flame sensed. Check sticking gas valve.
Rapid continuous blinking - Incorrect twinning, incorrect primary polarity. Reverse transformer secondary leads, reverse primary wires.
Closed pressure switch can be from dirty combustion vents, bad chamber pressure - like missing screws, maladjusted gas pressure, failing pressure switch, loose hoses, moisture in the hoses or fan blades The switch need to be closed to ge the unit to work
Posted on Jan 23, 2008
Tips for a great answer:
Oct 24, 2015 | Heaters
Feb 04, 2014 | Heaters
Dirt is the biggest enemy of your furnace. It can waste fuel and drastically lower efficiency. Dirt affects all three basic components of your furnace, so cleaning is the most important part of regular maintenance. The three parts of the furnace should be cleaned: the filter system, the blower, and the motor.
The furnace filter should be replaced or cleaned at the beginning of the heating season and about once a month during periods of continuous use. To check the filter, take it out and hold it up to the light. If it looks clogged, replace it with a new filter of the same type and size regardless of the length of time it has been used.
Step 4: Clean blower assembly, belts and pulleys to blower, and motor housing. Cleaning blower is critical if furnace has a squirrel-cage fan, because openings in this type of blower often become clogged with dirt. To clean blower, remove panel that covers filter to gain access to blower or panel on front of furnace. This panel may be slip-fit on hooks or held by series of retaining screws. Access to inside of blower is usually gained by sliding out fan unit, which is held on track by screws.
If power cord to fan assembly is not long enough to permit fan unit to slide all the way out, disconnect cord. Mark wire connections first so you'll be able to reassemble unit correctly. With toothbrush, clean each fan blade and spaces between blades. Then, with vacuum cleaner hose, remove all dirt and debris loosened by brushing. Vacuum belts and pulleys. Wipe motor housing clean to prevent heat buildup in motor.
Feb 08, 2013 | Rinnai Toyostove Direct Vent Heater:...
Nov 29, 2011 | Goodman Heaters
Oct 28, 2011 | Goodman Heaters
Oct 12, 2011 | Goodman GMS90703BXA Heater
Feb 03, 2011 | Goodman Heaters
Nov 10, 2010 | Dayton Gas Furnace Heater
Mar 12, 2010 | Heaters
1,364 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: