Question about Aprilaire 700 Humidifier
Water supply in humidifier always spraying onto filter when unit is turned on
Check your humidistat for proper operation, when full off,, you should get infinite ohms using an ohm meter. Make sure wires are not shorted on the humidistat. Quick test is to diconnect one humidistat wire and unit should never turn on. If it turns on, then it is not wired in series. If the water stops flowing when the voltage is not on, but water flows when energized then your solinoid IS GOOD and you must check your humidistat and furnace electrical connections.
Posted on Dec 26, 2009
I have the exact same problem. At this time I am looking for a new solinoid (part on the bottom) to install. Anyone else having this problem and know where to find replacement parts
Posted on Jan 26, 2008
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Mar 03, 2010 | Aprilaire 600 Humidifier
Jan 21, 2010 | Humidifiers
Jan 09, 2010 | Honeywell Humidifiers
Mar 05, 2009 | General Filters 1042-LH Humidifier
Feb 03, 2009 | Honeywell HE260A1010 Whole House...
Feb 01, 2009 | Honeywell HE360A1027 Whole House...
Nov 22, 2008 | Carrier SBP Humidifier
200 people viewed this question
Usually answered in minutes!