Question about Goodman GMS90703BXA Heater
I am confident the technician(s) have done this but check anyway.
Gas pressure 4-7 inches W.C for natural, 10 - 11 for Propane.
Air filter clean and unrestricted.
Temperature over supply plenum 140 degrees F.
All registers open and unrestricted.
Vent and intake unrestricted and not blocked.
Condensate hoses free of debris and draining.
OK now lets check to see if the furnace is staying on long enough.When it runs for a heat cycle, is the flame staying on until about 2 minutes prior to achieving the set temperature or is it cycling everyfew seconds and never reaching temp? To check you will need to view the flame through a small viewing port of thru the fins in the front door. Watch them for 10 to 15 minutes.
If they are staying on a long time, we will need to see if the room blower is working properly. If they are going out quickly and or cycling. Get the technician on the pone to talk it over. It could be a safety sensor.
If the blower stays on and the burners are on as well, you have a door open somewhere. Just kidding. Remove the thermostst documenting which wires go where. Take the white wire and cross it with the red wire. This will (or should) turn on the furnace. Clamp them together untill the either the house gets warm or you are confident it is not going to reach temperature. If it did get close to the temperature you wanted, it is a thermostat issue. If not, you got me!
And they say we have an easy job! Get beck to us with your results.
Posted on Jan 23, 2008
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 16, 2014 | Goodman Manufacturing Goodman Gas Furnace...
Nov 17, 2011 | Goodman Heating & Cooling
Jan 07, 2011 | Goodman GMS90703BXA Heater
Dec 02, 2010 | Goodman GMS90703BXA Heater
Dec 11, 2009 | Goodman GDS80904BNA Open Flame Heater
Dec 02, 2009 | Goodman GMS90703BXA Heater
Jan 20, 2009 | Goodman CLQ36AR49 Air Conditioner
Jun 08, 2008 | Goodman GMS90703BXA Heater
2,403 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: