Question about Heating & Cooling
Heat pumps provide good heat until the tempurature drops below 35-40 degrees. After that there isn't much heat to extract from the outside air and then either the gas furnace kicks in or the electric heat strip does the job of heating the air. if you have heat strips, I would check your breakers in your panel and sometimes there are a couple of breakers right on the air handler or furnace. The ones that will be for your heat strip are 220v and will be twice as wide as your normal 110v breakers . Please don't trust a visual inspection as they can look like they are in the "on" position but are indeed tripped. Turn them all they way off and then back on. If the beakers check out you may have an open cicuit in the heat strips themselves and you will need to have a qualified HVAC tech look at your furnace to repair it.
If your furnace is a "duel fuel" and uses natural or LP gas for back up heat then your ten year old rheem probably needs a good maintenance by a qualified service tech. There is a flame sensor to clean, ignitor to check (replaces the old school pilots), burners to clean flue connections to check and much more. ALL manufacturers of any heating apliance recommend yearly maintenance. Most companies offer something for around 100 bucks. I hope this helps.
Posted on Dec 13, 2009
Testimonial: "Rocco, this was the most thorough and helpful response I've seen from anyone so far... I tried justanswer.com and they really didn't help like this.TX"
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Dec 12, 2013 | Rheem 13PJL30A01-RHLLHM3617JA 2.5 Ton 14...
Nov 13, 2013 | Kia Cars & Trucks
Nov 11, 2013 | Honeywell RTH7600D Touchscreen 7-Day...
Jan 05, 2011 | Heating & Cooling
Jun 03, 2010 | Heating & Cooling
Jan 05, 2010 | Heating & Cooling
Feb 15, 2009 | Ruud UBHC Air Conditioner
Nov 24, 2008 | Weather King 12AJA4801AH Air Conditioner
261 people viewed this question
Usually answered in minutes!