Question about Heating & Cooling
Have a rheem criterion II. Model #RGPH-06EAUER....
Frquently, only the first of three burners / flames ignites and the cycle stops. Furnace cycles two or more times before all three ignite and furnace stays running. Tapping the gas line to the manifold encourages ignition of all three flames... I have cleaned all ports on the manifold and the filter remains clean....How do I remedy this?
The way it lights is that the gas is spread from one burner to the next by either a flame tray or small holes drilled in the burner tubes. If the flame does not get all the way across the burner tubes within a few seconds, the unit goes out on failure. Clean and inspect each burner tube, not just the orifice. Clean any tray that connects the burners. You can use a small wire brush or tooth brush but be careful near the glow igniter as it is very fragile.
Posted on Dec 12, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 16, 2015 | Heating & Cooling
Jan 08, 2013 | Heating & Cooling
Apr 04, 2010 | Heating & Cooling
Dec 30, 2009 | Heating & Cooling
Nov 15, 2009 | Heating & Cooling
Oct 29, 2009 | Rheem Paloma PH-20R IFSN / RTG-53PVN...
Jul 06, 2009 | Heating & Cooling
Mar 10, 2009 | Goodman GMS90703BXA Heater
Dec 25, 2008 | Heating & Cooling
829 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: