Question about Aprilaire 600 Humidifier
If your using an outdoor thermostat then it may not be connected properly or the manual mode resistor wires are touching. these are connected on the humidistat just to the right of the H H terminals
Posted on Dec 31, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 06, 2013 | Humidifiers
If your humidifier is equipped with a Digital Humidifier Control with Water
Panel change indicator, after replacing the Water Panel, turn the control
knob to the "Test/Reset" position until the "Humidifier On" light blinks to
reset its timer. (Blower must be operating and HVAC calling for heat.) Be sure
to turn the control knob back to it's original setting. If the "Humidifier On"
light continues to blink, your humidifier is in Test mode. DO NOT LEAVE THE
CONTROL IN TEST MODE OR HUMIDIFIER WILL NOT OPERATE.
Jan 27, 2011 | Aprilaire 400 Humidifier
Dec 17, 2010 | Aprilaire 600 Humidifier
Nov 17, 2010 | Aprilaire 700 Humidifier
Nov 01, 2010 | Aprilaire 600 Humidifier
Mar 10, 2010 | Aprilaire Humidifiers
Dec 13, 2009 | Aprilaire 700 Humidifier
Feb 16, 2008 | Aprilaire 600 Humidifier
Dec 24, 2007 | Aprilaire 700 Humidifier
May 22, 2017 | Aprilaire 600 Humidifier
459 people viewed this question
Usually answered in minutes!