Question about Cozy (W352E) Heater
Hi, have done this to many times not to know. I will walk you through this. It is good that the pilot is lit. Go to the stat and remove cover. Don't worry as this is a milivolt unit, no voltage or such a small amount you wont even notice as this is why it is called milivolts.Take a small screw driver to remove the next section which is the thermostat and will expose the sub-base where you will find 2 wires connected to it. You may have 2 or 3 screws to take loose to get to this last section. Anyway, if you have a piece of insulated wire laying around, even old speaker wire will work, take it and touch the wire across the 2 terminals and hold. If the furnace comes on, the thermostat is faulty, and you will need to buy a new one. No power to shut down, and simple to change. Cost about $12.00 dollars. Try and get a heat only milivolt stat as they are much less expensive and will have less problems with them. Go to home DEPOT to get one, or O.C.S.H. will also carry them. Don't let the salesman talk you into buying a programable heat and cool stat, 24 volts as they will work, but cost more and you don't need it!! Look around even if you need to go to a wholesale Refrigeration, Air Conditioning, and Heating parts house. Tell them you need one for a unit in some apts you own, and you will pay cash as you want a cash account. They will only ask what job its for, and just tell them your name. This is not illegal and I wouldnt tell you this if it was!! You will still have to pay taxes but will get a wholesale price for it. I am sure it will fire up when you touch the 2 wires and prove stat is bad. For some reason it is not the stat, follow the 2 wires from the stat down to gas valve and jump the same 2 terminals there also. If it fires up, you will have a problem in the wires from the stat to heater and will need to be replaced. I don't think this is the case. But, on the chance it will not fire after you have done all of the steps I have had you do, then you have a faulty main gas valve(MGV) and will need to replace. This is all easy to repair.I am a 100% sure it will fire up when you jump the 2 wires together, and you will need the stat. Please let me know as I will be waiting for an update! Good Luck,
PS When you install the new stat, make sure it is Level.
Posted on Dec 18, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 30, 2017 | Cozy Heating & Cooling
Feb 11, 2015 | Cozy Heating & Cooling
Sep 10, 2014 | Cozy Heating & Cooling
Oct 30, 2011 | Empire DV-35 Heater
Nov 27, 2010 | Cozy (W352E) Heater
Jan 30, 2010 | Cozy (W352E) Heater
Nov 06, 2009 | Cozy (W352E) Heater
Nov 08, 2008 | Cozy (W352E) Heater
742 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: