Question about Aprilaire Humidifiers
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
A bad circuit board should not make any noises. A bad solenoid valve could make a loud buzzing noise. If the noise is a squealing noise then you have defective bearings in the blower motor.
If you disconnect the low voltage wiring from the solenoid valve and you still hear the noise, then its not the solenoid valve.
Posted on May 10, 2009
A simple check you can perform on your aprilaire 760 is the following:
1) locate the two brown wires coming out of the 760 (these wires will be wired to tell the 760 to turn on when the hvac bower is on and the humidistat is calling for moisture).
2) temprarily disconnect the two brown wires from the external wiring and then short the wires together. All you're doing here is bypassing the your thermostat and bower-on indicator.
With the 70 unit plugged in to the wall outlet and the two brown wires connected together, both the fan and the solenoid valve (water inlet valve) should both be activated.
Posted on Dec 29, 2009
Tips for a great answer:
Feb 03, 2013 | Kenmore 14417 Humidifier
Feb 19, 2011 | Aprilaire 700 Humidifier
Mar 03, 2010 | Aprilaire 700 Humidifier
Feb 14, 2010 | Aprilaire 700 Humidifier
Dec 13, 2009 | Aprilaire 700 Humidifier
Apr 06, 2009 | Aprilaire 700 Humidifier
Jan 15, 2009 | Aprilaire Humidifiers
Dec 29, 2008 | Honeywell HE365 Humidifier
Nov 27, 2008 | Aprilaire 700 Humidifier
71 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: