Question about Honeywell CT87B ROUND HEATING&COOLING MECHANICAL THERMOSTAT - WHITE Heater
We have a round thermostat made by Honeywell. I would assume it is from 1992 or thereabouts ... the temp is set at 70 and the heat doesn't turn on even at 60. We notice that there is a ''dial'' on the inside of the round cover that has a thin metal 'arrow' pointing where numbers are printed on a metal band. Is this the threshhold for upper/lower temps? And if so, how do you adjust it????
The thermostat that you have is position sensitive. By that I mean that you need to have it in the right position for it to work correctly.
When you have the ring off of the thermostat loosen the two little screws and pull the thermostat away from the subbase. On the subbase you will see a line that needs to be level. If it is not level then the mercury bulb will not be in the right position to start and stop the furnace. Level the subbase and reassemble the thermostat and your furnace should start to work properly. If not then the thermostat is probbaly bad.
When they go bad it is often becasue ot the little arm that you refeered too. That is a small heater than actually fakes the thermosat into thionking that it is hotter in the room then it really is. This makes the furnaces shut down a bit early to combat overshoot. Adjusting that will determine how much time before the furnace hits the shutdown temperature that it will actually shutdown... got that?? In others ward it is probably a good idea not tp mess with that unless you know what you are doing. However the heater can burn out and create problems.
So, check that the thermostat is level and if not get a new t-stat...
I hope that this will help you to solve your problem!
Thanks for using Fixya!!
Posted on Dec 11, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 18, 2015 | Honeywell T87K1007 Mechanical Thermostat...
Dec 13, 2013 | Honeywell Heating & Cooling
Mar 11, 2013 | Heating & Cooling
May 31, 2010 | Honeywell Electronic Programmable...
Oct 23, 2008 | Honeywell Electronic Programmable...
Oct 22, 2008 | Honeywell CT87B ROUND HEATING&COOLING...
Jan 14, 2008 | Honeywell CT87B ROUND HEATING&COOLING...
Dec 01, 2013 | Honeywell CT87B ROUND HEATING&COOLING...
383 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: