Question about Goodman Heating & Cooling
Goodman GPM075-3. I need to know where the two wires from the outside compressor hook up on the board. The blue wire from the tstat (which controls the cooling) should connect with one of them. Where should these wires connect?
Your thermostat powers 'Y' for cooling. That in your case blue wire connects to 'Y' on the control board in the furnace. Then a pair of low-voltage wires connects 'Y' and 'C' on the furnace to the two wires to the coil of the contactor in the a/c condensing unit. So to follow the path, the signal wire from the thermostat sends 24v down the Y wire to the furnace board Y terminal which also connects to one side of the contactor coil in the air conditioner. To complete the control circuit to the air conditioner there has to be a common wire. This is connecting the C wire from the furnace board to the other side of the contactor in the air conditioner. Hope this helps.
Posted on Dec 11, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jul 25, 2011 | Goodman Heating & Cooling
Aug 26, 2010 | Goodman CLQ36AR49 Air Conditioner
Jul 17, 2010 | Goodman CKL24AR24 Air Conditioner
Jul 04, 2010 | GE AJCQ08ACB Air Conditioner
May 24, 2010 | Goodman CKL60AR60 Air Conditioner
Aug 18, 2009 | Goodman CLJ30AR32 Air Conditioner
Jun 01, 2009 | Goodman CKL36AR36 Air Conditioner
Apr 28, 2009 | Heating & Cooling
Jul 06, 2008 | Goodman CLQ36AR49 Air Conditioner
Oct 16, 2018 | Goodman Heating & Cooling
216 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: