Question about Honeywell Programmable Thermostat Heater
Honeywell thermostat TH6110D1021. Blower comes on when heat is called for and furnace ignites 10 seconds later. Call for heat should turn on burner motor, ignition in 10 sec. then blower in 75 sec. is the way it should run. How to set thermostat to get blower to come on after the 75 seconds instead of before ignition. Have checked system type 1 as 0 and 3 as 0.
Hi, You are right, fan is on a time delay in the heating cycle, and after burners fire that is when this delay comes into play. You have a preset factory temperature that determines the cycle on time for the fan, and the off time after the burners shut down also. This will not be in the thermostat, but in the fan/limit control the is mounted on the face of the furnace, with a probe inserted into the fire box.Depending on how old or new this unit is, will depend on the type control you have.It may be just a high limit switch, or the 1st I mentioned.If so, It rotates in the burner as the temperature rises, to turn the fan on and off.Disconnect power, remove cover, and 2 screws.Slowly remove the control and gently clean the probe. Turn the dial if this one has it and you will be able to hear it click. This click is contacts closing to start fan operation.Reinsert and try again. If problem continues, you will have to replace it.They do tend to stick closed/on, in the heat cycle from time to time and a cleaning sometimes will solve this problem. Not knowing how old this furnace is and type, make it difficult to give you a correct diagnosis, so check this fan control as I have explained, and if your system is of a different type, please let me no so I can correct this problem. Sincerely,
Posted on Dec 11, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Feb 14, 2015 | Honeywell T87K1007 The Round...
Dec 14, 2013 | Honeywell Programmable Thermostat Heater
Nov 06, 2013 | ICM286 Furnace Control Board
Oct 15, 2010 | Honeywell Programmable Thermostat Heater
Jun 19, 2010 | Honeywell Electronic Programmable...
Mar 07, 2010 | Honeywell Programmable Thermostat Heater
Dec 07, 2009 | Honeywell Electronic Programmable...
Jan 02, 2009 | Honeywell Programmable Thermostat Heater
Jun 29, 2016 | Honeywell Programmable Thermostat Heater
357 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: