Question about Goodman Heating & Cooling
When the furnace is running the light comes on, lights all 4 burners but only lasts a couple seconds. This goes on the entire time it is running. Took off the door and followed directions to turning switch to off, leave for 5 min. turn on, replace door and set therm. to low heat. have done all this and as soon as the fan kicks on the flames go out.
If the flame lights all the burners within 2 seconds but does not stay on, you may need to clean the flame rod found at the farthest end of the burner box. It will be located at the end of the box that lights last. It will be a probe that is in the flame of the last burner. If it has carbon on it or scale, take an old tooth brush and scrub it. Check the wire connected to it and follow that wire back to the circuit board and check that connection.
Posted on Dec 11, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Dec 26, 2016 | Heating & Cooling
Jan 24, 2011 | Heating & Cooling
Mar 30, 2010 | York Furnace Draft Inducer Blower Fasco #...
Jan 27, 2010 | Heating & Cooling
Jan 10, 2010 | Heating & Cooling
Nov 28, 2009 | Carrier 38CKC042 Air Conditioner
Jan 06, 2009 | Heating & Cooling
Nov 22, 2008 | Heating & Cooling
Sep 05, 2008 | Heating & Cooling
Aug 27, 2008 | Intertherm Heating & Cooling
Oct 16, 2018 | Goodman Heating & Cooling
134 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: