Question about Water Heaters
Possible problems not knowing age of unit the
control valve could be sticking open allowing gas to continue to flow until high limit is reached and shuts down valve another possible problem with the newer style back flow preventer being install by water companys the rapid heating and expansion of the water over pressures the water system causing releif valve to pop open and reclose most water heater manufacters are recommending instalation of an expansion tank to allow the growth in volume of water somewhere to go is valve constantly leaking or only during heating cycle if you could supply additional information does unit only leak when heating
or is steam expelled when releif valve opens
t-stat not opening gas valve sticking partially open
bad high limit bad pressure releif valve no expansion tank to allow for thermal expansion if steam is present and unit is boiling water inside replacement of water heater for safety concerns,would be reccomended if only water and pops couple of times water temp not over 140 degrees after most hot water has been used out of tank and is reheating most of capacity probably lack of expansion tank as the releif valve is the final safety device on a water heater is of great concern
the temp control gas valve or high limit are supposed to shut unit done long before the safety limit of releif valve is reached
Posted on Dec 11, 2009
Testimonial: "Tank is 15 yrs old, air temp has been 6-7 deg's. Repair or replace? Thanks for your help."
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Sep 19, 2014 | Water Heaters
Aug 03, 2014 | Bradford White M-I-5036FBN 50 Gallon -...
Oct 08, 2013 | Water Heaters
Hot water pressure relief valves serve two functions. The first is to remove high-pressure water from the hot water tank. The second function is to act as a high temperature valve to remove water that exceeds a predetermined point for the valve. Both of these relief settings are preset at the valve factory. Many pressure relief valves will come with a metal tag that identifies these release points. If you're attempting to remove the hot water heater pressure relief valve, pay careful attention to ensure that you replace with the correct valve.
Your hot water heater has a pressure relief valve safety mechanism. When pressure inside the water tank exceeds certain limitations, the valve opens up to allow the pressure to be released. A faulty pressure relief valve will not release excess pressure, which could cause extensive damage to your home. You should test the hot water heater pressure relief valve once every six months to ensure proper operation. If the pressure relief valve fails the test, replace the valve with a new one immediately
Locate the pressure relief valve on your hot water heater. The pressure relief valve has a lever handle on top with a drain pipe attached to it. The pressure relief valve is most often on the side of the water tank toward the top. Newer models of hot water heaters have the pressure relief valve on top of the water tank.
Inspect the area around the pressure relief valve for signs of leaking water. If there is leaking water near the relief valve connection, replace the relief valve. If no leaking is evident, proceed with testing the pressure valve.
Examine the area below the pressure relief valve drain pipe. Most water heater closets either have a drain in the floor below the pipe or the pipe is inserted into another pipe to direct the water out of the home. If the end of your drain pipe is not in another pipe or there is no drain in the floor, place a bucket under the drain pipe to catch water when you test the pressure relief valve.
Pull the lever handle on the top of the pressure relief valve up with your fingers. A working lever will lift up without difficulty.You should begin to hear water going through the drain pipe. Slowly release the lever to shut off the pressure relief valve. The pressure relief valve is good. If you did not hear water running through the drain pipe, lower the lever on the pressure relief valve and replace the valve. If the lever is difficult to raise, do not force the lever. Replace the pressure relief valve.
Feb 04, 2011 | Whirlpool Water Heaters
Jan 30, 2011 | Rheem Water Heater Pressure Relief Valve
Nov 17, 2010 | RTO Atwood Water Heater - 6 Gal LP
Jun 17, 2010 | RTO Atwood Water Heater - 6 Gal LP
May 25, 2010 | RTO Atwood Water Heater - 6 Gal LP
Jan 04, 2010 | Bosch AquaStar 125FXKIT-LP 125FX Liquid...
162 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: