Question about Coleman Propane Forced Air Heater w/Electronic Ignition (50,000-80,000 BTU)
The problem is withthe venting. Your vent pipe goes out of the house in such a way as to catch the air when it is windy and cause the pressure switch to cut out. The flame may only run for a short time, then shut down and then restart. The heat exchanger never gets hot enough to give you warm air.
Check where the vent pipes exit the house. Try adding on an elbow and turning it so that the wind cannot blow back the pipe. Turning it down towards the ground often is good. Make sure that the exhaust cannot recirculate back to the intake pipe also.
Also check that there is no water build up hanging in a pool where the vent pipe may have sagged a bit. this will make the pressure switch much more sensitive.
I hope that this will help you to solve your problem!
Thanks for using Fixya!!
Posted on Dec 11, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jan 01, 2013 | Coleman Home Electric Furnace Eb15b/Eb15d
Feb 21, 2011 | Goodman Heating & Cooling
Feb 05, 2011 | Heating & Cooling
The flame sensor is dirty or bad...it is not telling the control that the flame is lit...
is a tip that will help you try to figure out why your furnace is not
Basic Furnace or Heating System Troubleshooting
Feb 02, 2011 | Heating & Cooling
Feb 20, 2009 | Coleman Propane Forced Air Heater...
Nov 29, 2008 | Heating & Cooling
May 15, 2014 | Coleman Propane Forced Air Heater...
1,341 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: