Question about Heating & Cooling
If this si what I am thinking it is, it will be very hard to find and prove....
The compressor windings have aflat spot and if the motor stops at the right place it will not atart. The voltage goes way up and kicks out the thermal over load and gives you the alarms that you are getting.
The motor cools down and you reset the unit, the motor has moved just a tick trying to start the last time so now it is off of the bad start spot and will take off and run till it stops at the bad spot again....
Did that make any sense???
Long story short your compressor is going bad...problem will be to get it changed under waranty and convincing the installing company that you have a problem that requires a compressor replacement...
See if you can get them on a short leash and have them come before you reset the alarms and hopefully maybe they can catch what it is doing...
This is and will be a tough one... I've been there with a customer or two already... no fun... trying to figure things like this out!
I hope that this will help you to solve your problem!
Thanks for using Fixya!!
Posted on Dec 11, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jun 13, 2015 | Carrier Heating & Cooling
Nov 13, 2012 | Heating & Cooling
Jun 04, 2011 | Amana Heating & Cooling
Feb 03, 2011 | Heating & Cooling
Oct 04, 2009 | Briggs & Stratton Lawn-Boy Insight Series...
Sep 12, 2008 | Heating & Cooling
Mar 04, 2017 | Carrier Heating & Cooling
Jul 13, 2008 | Carrier Heating & Cooling
Dec 11, 2018 | Heating & Cooling
195 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: