Question about Heating & Cooling
Hi, What is happening is the control wiring from this thermostat is touching on the heat side from somewhere in the wall back to the furnace, so it calls for heat. It gets its power from the transformer on the furnace. Try disconnecting it at the furnace and it will shut down. If this is heat only, should have only 2 conductors and they would have to be touching somewhere. Look carefully at the wiring behind the stat and around the furnace for it may have melted together or bare spots where it is touching. This is the only thing that would make it come on with out the stat. Please let me know what you find. You can also ohm the red and white out to see if there is continuity, and if so, they are touching and you will either need to find it or run a new set of stat wires to solve this. Get back to me. Good Luck,
Posted on Dec 10, 2009
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Jun 06, 2017 | Honeywell Heating & Cooling
Dec 01, 2015 | Thermostats Heating & Cooling
Feb 20, 2015 | Heating & Cooling
Oct 06, 2014 | Coleman Dometic Duotherm Rv Air...
Mar 03, 2011 | Coleman Heating & Cooling
Jan 08, 2010 | Aprilaire Humidifiers
Dec 23, 2009 | Honeywell Electronic Programmable...
Sep 11, 2009 | Ruud Central System Air Conditioner
Nov 14, 2018 | Heating & Cooling
45 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: