Question about Procom Heating & Cooling
Can lite pilot by hand when it warms up and gets to end of cycle the pilot goes out
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: Laars Lite heater not working
1st time this happened to me the filter wasn't clean. 2nd time it was the pressure switch and for the third time they say I have to bleed the gas line, not enough gas to lite. And I also need the on/off switch gone bad.
Posted on Jun 15, 2008
SOURCE: my heater wont stay lit
Chanches are the thermal couple a safty divice is gone bad. they don;t cost a big bunch and the parts store at a local propain dealer may show you how to install it. its no biggie. Good luck. DFD
Posted on Apr 13, 2009
There are basically three things that can go wrong with the Warm Morning .
Sensor shut off. There is a sensor button on the back of the unit with a wire going from it to the thermocouple. This sensor turns the heater off if the flue is blocked, however it will also shut the heater off if the wire contacts are dirty, or if the sensor has gone bad.
You can test this by bypassing the sensor. Disconnect the two wires from the sensor and reconnect them directly together. If the pilot stays on, your problem is here. Try cleaning the wire contacts first.
Pilot orifice. If the pilot flame is small and doesnt look healthy, the pilot orifice may need cleaning. The hole is very small and can get dirty. Disconnect the silver tube and clean with electrical parts cleaner. Never try to clean the hole with an object like a pin, you may damage it. You may have to slide out the burner unit to get at the silver tube. (Always shut off gas before disconnecting lines and after you reassemble, spray joints with soapywater and look for small bubbles which may indicate a gas leak. Dont use parts cleaner around an open flame.)
Thermocouple can go bad but this is not as common as the first two problems.
Posted on Jan 28, 2010
Tips for a great answer:
Jan 05, 2018 | Heating & Cooling
May 28, 2013 | Raypak Pool & Spa
Jan 22, 2013 | Mr. Heater Big Buddy Heater
Oct 08, 2012 | Desa International Unvented Gas Space...
Aug 12, 2012 | Water Heaters
Jun 09, 2012 | Teledyne Laars Laars Lite 2 Pool Heater...
Mar 14, 2011 | Rheem 40 Gallon FVR NATGAS Low WATER...
792 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: