Question about Haier Energy Star ESA3183 Air Conditioner
Heat pump runs after resetting breaker until it cuts off then breaker kicks.
The start capacitor is bad. Motors develop what is known as lock rotor amperage. requires alot of torque to turn the motor until it reaches iits rated or run load amperage. the motor is not able to overcome the lock rotor amps which is usually 5x the rated amperage and always more amps than the breaker. this is usually not a problem because the start capacitor helps overcome the LRA so quickly that it doesnt trip the breaker. If the capacitor is round and bad it will be bulged at the top, if it is oval shaped then the rupture disc on top will be blown letting all the dielectric fluid out which cools the capacitor
Posted on Dec 15, 2009
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Oct 29, 2017 | Intertherm Heating & Cooling
Aug 11, 2015 | KitchenAid Dishwashers
Jan 21, 2013 | Heating & Cooling
Jun 08, 2017 | Ruud Matching Split Air Conditioner
Jul 09, 2010 | Fedders C36ACD1VF Split System Air...
May 02, 2010 | Heating & Cooling
Oct 27, 2009 | Intertherm Heating & Cooling
Apr 24, 2009 | Ruud Central System Air Conditioner
Nov 20, 2007 | Ruud Central System Air Conditioner
218 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: