Question about Fujitsu 36CS Air Conditioner
I have a 3 ton cooling only unit that will only work down to 0 degrees F. I know this is the factory limit but the problem is the unit cools a server room. I need to make this unit run at a colder temp. I was thinking of interupting the outdoor air thermister with a 75 k ohm resistor. Will this work?
75k ohms resistor is lower than 0 degrees F in equivalent temperature may be compressor cannot operate because the maximum setting of thermostat. is from 17 to 18deg. C. You can use 11 to 12k ohms the temp. for this is about 23 to 24 deg. C. The resistor resistance is fixed so the compressor continue running without cut out. The only problem for this is the compressor, because the design of the compressor is for high temp. Continue running of compressor can produce icing in suction and evaporator coil and cause damage of compressor due to liquid slugging.
Posted on Jan 17, 2008
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Nov 04, 2015 | GE Refrigerators
Jun 15, 2014 | Comfortmaker G8MXN0701716A 66,000 BTU 80%...
Apr 18, 2017 | Heating & Cooling
Jan 19, 2012 | 2002 Chevrolet Malibu
Apr 09, 2011 | Goodman CPLE24-1 Air Conditioner
Jul 02, 2010 | Weather King 10AJA6001AH Air Conditioner
Jun 07, 2010 | Goodman CLQ36AR49 Air Conditioner
Oct 17, 2009 | Frigidaire FAA055N7A 5200 BTU Room Air...
Jul 22, 2009 | Ruud UAKA042 Air Conditioner
May 18, 2008 | Danby Portable Air Conditioner
142 people viewed this question
Usually answered in minutes!