Question about Honeywell Heating & Cooling
My home furnace has a Honeywell gas valve has a marking on the side ( model V800 A1070 ) It is making rapid ticking noises and when it stops, the burners will light up until the valve starts ticking again, then the burner goes out. what can I do? If I have to replace it, can it wait til morning or does it need immediate attention tonight? and what model number can I use to replace this one?
A 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
The service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
I called Nexgrill technical support at 1-800-913-8999. They are sending me a new thermo couple to keep the valve open when ignited - so the patio heater will stay on. I needed to give them the serial number (inside the propane tank door) and fax them a copy of the receipt.
Hope this helps.
Posted on Jul 18, 2008
Is this furnace standing pilot or electronic ignition. If standing pilot i would check furnace filter then the thermastat. To test themostat first turn power off to furnace. Take thermostat off wall and take wires labled R & W and connect them together. If you have electronic ignition I would start with cleaning the flame sensor with steel wool or wire brush.If you have and more questions i will be glad to help.
Posted on Jan 17, 2009
The click you hear is the gas valve shutting off flow. It does that because the thermocouple (a rod sticking into the flame of the pilot) voltage drops, usually below 13 millivolts or so. Might be a loose connection from thermo to valve body (should be finger tight plus 1/4 turn) or a bad thermo ($13 at Lowe's). Good Luck.
Posted on Dec 04, 2009
Hi, the howling you describe is pretty common as gas heaters first come on. NG or LP gas is delivered at a pressure much higher than appliances actually use, step down regulators lower the pressure as the gas flows. So, when you first turn your heater on, the pressure is a little high until the flow causes an equalization of pressure. You could contact your gas supplier and ask them to check your pressure and tell them you suspect a building regulator. If the pressure were to build too high it could cause leaks or damage the appliance controls. Good luck.
Posted on Jan 10, 2010
Looks like an older system. Tighten all of your electrical connections. Inspect all of the low voltage wiring for any insulation cracks or other damage. The problem you describe sounds like something is either "shorting" or breaking down electrically. Unless the technician can catch it while he/she is there, it will be difficult to determine exactly what is happening. You might get lucky and resolve it yourself by tightening all electrical connections and reinsulating (use electrical tape) any damaged low voltage wire connections. If you continue to experience problems, get the tech. Hopefully the last company you used will be willing to work with you on the bill considering they were unable to "catch" it during the last visit.
Without being there with toolbox in hand, I hope you find this information very helpful moving forward. :-)
Posted on Mar 19, 2010
Testimonial: "Thanks for taking the time to answer my inquiry. I'll let you know how it works out."
Tips for a great answer:
Mar 25, 2018 | Honeywell Heating & Cooling
Nov 18, 2013 | Honeywell Furnace Gas Valve Sv9501h2409
Feb 25, 2018 | Honeywell Furnace Smart Gas Valve Sv9640m...
May 02, 2011 | Honeywell TH4210D1005 Heater
Jan 17, 2011 | Heating & Cooling
Mar 20, 2010 | Heating & Cooling
Mar 11, 2010 | Honeywell Heating & Cooling
Dec 30, 2009 | Kitchen Appliances - Others
Nov 02, 2009 | Honeywell Power Humidifier: Furnace...
Jan 16, 2008 | Hunter Fan Company 5/1/1 Programmable...
214 people viewed this question
Usually answered in minutes!