Question about Rinnai RHFE-431FAIII 16,700 BTU Direct Vent Furnace Energy Saver Heater - Natural Gas
OK, sounds like a sensor problem to me. The temperature reading is done on the backside of this unit. Remove the top cover and with a flashlight in hand, look for a small black rubber probe with yellow wires attached. You will find it about 2 inches above the floor and on the right hand side (when viewing from the front). Make sure this probe is not being influenced by the venting system and showing a “false” reading. If the vent pipe (the one covered by cloth) is close to it, the probe is made that you can relocate it out of the way of the vent. You will need to get to both the backside of the heater and go inside the heater cabinet to do this properly. If the vent is a few inches away and not influencing the probe, place a cold cloth on the probe and see if the temperature drops. Then a warm clothe on it to see if it rises. You could have a bad probe. List your model number and I can get you a part number.
Posted on May 16, 2008
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
Tips for a great answer:
Aug 29, 2018 | Heating & Cooling
Apr 21, 2018 | Intex Pool & Spa
Mar 09, 2018 | Heating & Cooling
Jan 10, 2011 | Intertherm Heating & Cooling
Dec 19, 2010 | Goodman PHKJ024-1 Air Conditioner
Jun 23, 2009 | Honeywell Programmable Thermostat Heater
Mar 04, 2009 | Hunter Fan Company 7-day programmable...
Jan 25, 2009 | Amana PTH123B25AJ Heat Pump Air...
Sep 23, 2008 | Rinnai RHFE-1004FA 38,400 BTU Energy Saver...
Jan 20, 2008 | Rinnai Vent Free Gas Heater/: 6,000 BTU...
Jun 29, 2014 | Rinnai RHFE-431FAIII 16,700 BTU Direct...
77 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: