Question about LG LSC121PMA Split System Air Conditioner
Remote control units have diagnostic program in the
control, after 3 to 5 minutes of operating if the diagnostic
tools detect abnormal operation, then its shutdown the unit
to protect from damage. Thermistor sensor is one of the
parts that detect the operation of the unit. Out of range
or defective thermistor can shut the operation of the unit.
- If your indoor and outdoor is clean start the unit in cool mode and monitor the outdoor pipes. If your suction pipe is icing or dry then your unit is under charge, but if your suction is cold and sweating then the system is ok and sure that the thermistor sensor is defective.
- Out of range thermistor sensor in both return air and freeze up sensor can cause the tripping “off “ the unit. The resistance of both thermistor is 8 to 10k ohms, so can test by using ohm meter
Posted on Jan 12, 2008
Tips for a great answer:
Jul 17, 2015 | Air Conditioners
Jul 31, 2013 | Ruud UBHC Air Conditioner
Jan 24, 2013 | Fujitsu 24C1 Air Conditioner
Mar 31, 2011 | Carrier Air Conditioners
Jan 28, 2011 | LG Air Conditioners
Jan 22, 2011 | Ruud UAKA042 Air Conditioner
Jul 05, 2010 | LG LSC183VMA Split System Air Conditioner
May 22, 2009 | Frigidaire FSC23R5SBK Air Conditioner
Jan 03, 2009 | LG LSC121PMA Split System Air Conditioner
Jun 22, 2008 | Goodman CLJ30AR32 Air Conditioner
768 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: