Question about Goodman GDS80904BNA Open Flame Heater
I have a goodman furnace and it's working, but not blowing hot air. The red light on the control panel is blinking 3 times, indicating that my pressure switch is open. Can anyone tell me how to find the pressure switch please?
Its not on the gas valve it's the device with the hose connected to it on the front above the gas valve and behind the draft blower. the hose goes from the pressure switch to the draft blower. usually not the pressure switch though. the circuit boards are notorious for burning up and giving a false diagnostic code. if it is the pressure switch remove the hose and try to blow it out and then connect it to the switch again leaving the other end off the blower. Blow gently into the hose and listen to the switch to see if it clicks. try sucking and removing any obstruction. if it does not click back and forth then it is bad.
Posted on Dec 12, 2009
It's mounted onto the gas valve. It will be a button or lever that you have to push in or down, depending on the style.
Posted on Nov 20, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Jan 19, 2016 | Goodman Manufacturing Goodman GMS81005CN...
Jan 24, 2008 | Goodman GMS90703BXA Heater
Mar 18, 2014 | Heating & Cooling
Jan 21, 2014 | Goodman Heating & Cooling
Here is a tip that will help you try to figure out why your furnace is not working.
Basic Furnace or Heating System Troubleshooting
Jan 24, 2011 | Goodman Heating & Cooling
Jan 20, 2011 | Goodman Heating & Cooling
Mar 22, 2017 | Goodman Heating & Cooling
Mar 27, 2010 | Goodman Heating & Cooling
Jan 10, 2010 | Goodman GDS80703ANA Open Flame Mid-Size...
Oct 17, 2009 | Goodman Heating & Cooling
503 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: