Question about Kitchen Appliances - Others
Save hours of searching online or wasting money on unnecessary repairs by talking to a 6YA Expert who can help you resolve this issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
Here's a link to this great service
Posted on Jan 02, 2017
SOURCE: Thermastat and furnace
you should have 24 volts between yellow and white wires at the stat when the stat is set to heat and set as hot as it will go. burners should light first then 3 to 5 minutes later the fan motor should fire up. if burner doesn't light check the wires going into the top of the gas valve see if you have 24 volts arriving there from the stat. if you do then the gasvalve is probably bad. you can bypass the action of the stat by jumping red to white on 90 percent of the stats made and in a few seconds the gas valve should click open gas flow to main burner where pilot ignites it. another easy check you can do is flip stat fan switch to on. fan should come on at once. if not then you have either no high voltage to unit or no low voltage ( as in a bad transformer). if the fan comes on you know you have high volts and low volts...by cover i assume you mean the decorative cover but there second cover with the mercury bulbs and all is still there. if you have only the bare subbase then new stat time. sounds like an old furnace if it has a standing pilot, it should be checked for cracked heat exchanger by a pro with a n electronic carbon monoxide detector. NOT a diy item due to the real danger of co poisoning.
Posted on Oct 09, 2008
Hi , you can try and pull the panel on the bottom of fireplace out and check the adapter in fireplace. Sometimes they go bad. When you open in also check to see if there is an adapter plugged in and a option to use the battery operated function. If this goes bad the pilot will not stay lit.
Posted on Jan 14, 2009
SOURCE: Marco gas fireplace shuts off
This an easy fix. What you must do is remove the dust from the pilot safety. I use rust buster from ace hardware to gently flush the hole. If ther is no hole just shoot a tiny drop or 2 into the pilot burner where the flame comes out. Blow it out (I use a piece of tubing). The problem is the dust drops the pilot flame to a point where it won't heat the thermocouple hot enough to jold the magnet and after 30 minutes she quits. THIS is a picture of where to clean the ODS pilots in your rig.
If you need further help, reach me via phone at https://www.6ya.com/expert/dan_73bbd84fe1d95b61
Posted on Feb 09, 2009
Tips for a great answer:
Dec 07, 2015 | Heating & Cooling
Jan 18, 2015 | Home
Nov 12, 2012 | Heating & Cooling
Apr 29, 2011 | Heating & Cooling
Mar 25, 2011 | Heating & Cooling
Nov 27, 2010 | Heating & Cooling
Mar 25, 2009 | Leisure HOMEPRIDE Electric Fireplace...
Dec 28, 2008 | Heating & Cooling
Nov 20, 2007 | Leisure HOMEPRIDE Electric Fireplace...
670 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: