Question about Traulsen 46 cu. ft. Commercial Freezer G22001
Most all commercial freezers have a fan delay/ defrost terminator. It is usually mounted on the end of the evap coil. It's purpose is to sense the temp of the coil during the defrost cycle. When it hits a preset temp., usually around 55 degrees or more (depends on Mfg.) It terminates the defrost cycle. It also doubles as a fan delay. It allows the evap coil to cool off from the defrost cycle before allowing the fan to come on. Usually, the coil has to get around 20 degrees before fan will energize. I would look for this as a possible problem. It could be one device with 3 wires or 2 separate devices with 2 wires each. I've seen it both ways.
Hope this helps.
Posted on Nov 20, 2009
Testimonial: "This is much in line with what the tech said. He will be back tomorrow to fix this part. "
a 6ya expert can help you resolve that issue over the phone in a minute or two.
Best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of.(from cars to computers, handyman, and even drones)
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Aug 12, 2011 | Hoshizaki Commercial Freezer SafeTemp®...
Dec 10, 2010 | Frigidaire 20.3 Cu. Ft. Frost-Free Upright...
Oct 23, 2009 | Electrolux Freezers
Oct 04, 2009 | Frigidaire 14.1 cu. ft. Upright Freezer...
Sep 15, 2009 | Frigidaire 20.6 cu. ft. / 583 liter...
Sep 03, 2009 | Freezers
Aug 22, 2009 | Freezers
Aug 13, 2009 | Nor-Lake Freezer Norlake Refrigeration 6'...
Jun 13, 2009 | Freezers
418 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: