Question about Honeywell HE360A1027 Whole House Humidifier Humidifier
I have a 90+ carrier furnace and I installed a by-pass type humidifier. I figured I would use the existing wiring which was powering a drum type humidifier but the 3 amp fuse popped on my furnace board from the load from the water solenoid on my new humidifier. I don't want to increase the amperage of the fuse. Do you have any ideas? The new humidifier came with a 24 volt transformer but then it would require to be tapped into a "furnace demand" circuit somewhere.
Thanks for your help.
Hook up the new transformer to the white (common) from the blower motor, and the lead from the blower motor hooked up to the heat term on the board. (just cut the wires and wire nut all three together)
Posted on Nov 18, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Feb 22, 2013 | Carrier Humidifiers
Jan 31, 2013 | Aprilaire 400 Humidifier
Jan 30, 2011 | Carrier LFP Humidifier
Jan 19, 2011 | General Filters 1042-LH Humidifier
Jan 19, 2011 | Carrier SBP Humidifier
Mar 01, 2010 | Carrier LBP Humidifier
Dec 08, 2009 | Honeywell Humidifiers
Jan 11, 2009 | Honeywell Power Humidifier: Furnace...
Dec 07, 2008 | Honeywell Power Humidifier: Furnace...
Nov 22, 2008 | Carrier SBP Humidifier
Jul 11, 2017 | Honeywell HE360A1027 Whole House...
Jan 09, 2014 | Honeywell HE360A1027 Whole House...
650 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: