Question about Sta Rite Sta-Rite Max-E-Therm High Effiency - Propane Heater - 333,000 BTU
The wrong orifice was installed. Sta-Rite changed their blower configuration 3 years ago. Heaters older than that have a flat orifice that works with the older style blowers. Newer heaters are equipped with a tapered orifice. Mixing a flat with a new blower causes whistling. Mixing a tapered with an old blower causes whistling. Good luck!
Posted on Dec 04, 2009
Posted on Nov 18, 2009
a 6ya expert can help you resolve that issue over the phone in a minute or two.
best thing about this new service is that you are never placed on hold and get to talk to real repairmen in the US.
the service is completely free and covers almost anything you can think of (from cars to computers, handyman, and even drones).
click here to download the app (for users in the US for now) and get all the help you need.
Posted on Jan 02, 2017
Tips for a great answer:
Nov 10, 2014 | Rheem Tankless Hot Water Heater...
on Dec 10, 2010 | Kenmore 40494 / 40495 / 40499 Electric...
Sep 14, 2014 | Water Heaters
Sep 13, 2014 | Rheem 40 Gallon FVR NATGAS Low WATER...
Jan 28, 2014 | Lincoln Ovens
Jan 28, 2014 | Ovens
Sep 14, 2011 | Barbeques Galore Capt'n Cook 3-Burner...
Dec 10, 2010 | Heating & Cooling
Nov 21, 2010 | Coleman Propane Forced Air Heater...
Nov 20, 2009 | Dyna-Glo D-E37 Wall Mounted Panel Heater
Oct 20, 2012 | Sta Rite Sta-Rite Max-E-Therm High...
530 people viewed this question
Usually answered in minutes!
Step 2: Please assign your manual to a product: